×

transformer excitation current readings

1. Junior Member
Join Date
Jan 2016
Posts
7
Reputation

transformer excitation current readings

During the performance of an excitation current test on a power transformer, you notice that two of the currents are higher than the third reading. Why?

2. Junior Member
Join Date
Jan 2016
Posts
3
Reputation
Originally Posted by kcorpuz
During the performance of an excitation current test on a power transformer, you notice that two of the currents are higher than the third reading. Why?
It is due to transformer core reluctance which is proportional to current. Voltage that you apply for testing is constant therefore magnetic flux.
E(voltage) = 4.44 f*N(number of turns)*F(flux)
Voltage must be constant to keep Flux constant. Number of turns is fixed.

Now, N(number of turns)*I(current) = F(flux)*R(core reluctance)

Higher reluctance then higher current and opposite. Reluctance is lower for the center leg of transformer therefore current is lower. Two legs (one on each side) have higher reluctance and therefore have higher current value.

Last edited by Artonic; October 29, 2018 at 06:27 AM.

3. Junior Member
Join Date
Jan 2016
Posts
7
Reputation
Originally Posted by Artonic
It is due to transformer core reluctance which is proportional to current. Voltage that you apply for testing is constant therefore magnetic flux.
E(voltage) = 4.44 f*N(number of turns)*F(flux)
Voltage must be constant to keep Flux constant. Number of turns is fixed.

Now, N(number of turns)*I(current) = F(flux)*R(core reluctance)

Higher reluctance then higher current and opposite. Reluctance is lower for the center leg of transformer therefore current is lower. Two legs (one on each side) have higher reluctance and therefore have higher current value.
Thank you the respond. That for sure helps a lot.

or to leave a reply!

Related Content