×

# How to Size Transformer Neutral Resistor

###### Jump to latest post
1.  Junior Member
Join Date
Dec 2014
Posts
6
Reputation ## How to Size Transformer Neutral Resistor

Can someone explain how to size a transformer neutral resistor for limiting fault current? For example: What size neutral resistor would be required to limit the fault current of a 13,800-480Y/277V 1500kVA Transformer to 200A?  Reply With Quote

2.  Junior Member
Join Date
Jan 2016
Location
NJ
Posts
19
Reputation This question comes from the level 2 practice exam..!?

im curious my self

Dan  Reply With Quote

3. Originally Posted by AlexT90 What size neutral resistor would be required to limit the fault current of a 13,800-480Y/277V 1500kVA Transformer to 200A?
Simple ohms law. Use line-to-neutral voltage: 277 volts / 200 amps = 1.385 ohms  Reply With Quote

4.  Junior Member
Join Date
Feb 2016
Posts
1
Reputation ## Neutral Ground Resistor Originally Posted by AlexT90 Can someone explain how to size a transformer neutral resistor for limiting fault current? For example: What size neutral resistor would be required to limit the fault current of a 13,800-480Y/277V 1500kVA Transformer to 200A?
277 V/200 A=1.385 OHMS to limit the ground fault current to 200 A on the 480Y/277 V system.

Some related information in case you are designing a resistance grounded system as opposed to answering a test question:

1. A 200 A max ground current limit would be more appropriate for a MV system (e.g., 4.16Y/2.4 kV).

2. In a LV system, a high resistance grounding scheme is employed with a resistor typically sized to limit ground fault current to < 10 A (the current must be > the system capacitive charging current e.g., cables, motors, transformers,.. capacitances).

3. The minimum size of the conductor from the supply transformer neutral to the neutral grounding resistor is stated in the NEC.

4. When investigating HRG system viability there are some application considerations such as:
• line to neutral loads like 277 V lighting must first be supplied via an isolation transformer's
• overvoltage protection of adjustable speed drives can be problematic

Several manufacturers have NGR whitepapers on the internet.  Reply With Quote

5.  Junior Member Pro Subscriber
Join Date
Dec 2018
Posts
5
Reputation ## Sizing a resistor to limit Ground fault current

this Question came on the NETA 2 practice test and I am wondering if there is a different approach to what i have. here is the question

11. What size neutral resistor would limit the fault current of a 4.16Y/2.4 kV 3000kVA Transformer to 200A?

My reasoning.
the Y on 4.16Y tells me it is a Y configuration, therefore between the common point of my three windings and the ground, i will put a resistor and a current of 200A going through it from the Y winding common point to the ground.

- Now the voltage in a Y configuration is as follow VLine = 1.73 Vphase. A this point I am interested in the Vph which is; Vphase= Vline/1.73 => Vphase = 4160 /1.73 = 2402v. This voltage is the one i will have from the uncommon leg of one winding to the ground. At this point have ohm law of one unknown resistor in series with one winding with a voltage of 2402v across them. Since, the winding infos are not given i will neglect that and just divide my phase voltage by the limiting current doing so, R=2402/200 =12.01 ohm as suggested by Testguy correct or no? thanks  Reply With Quote

6.  Junior Member
Join Date
Dec 2017
Posts
2
Reputation ## Error in voltage assumption Originally Posted by joeldjiogo this Question came on the NETA 2 practice test and I am wondering if there is a different approach to what i have. here is the question

11. What size neutral resistor would limit the fault current of a 4.16Y/2.4 kV 3000kVA Transformer to 200A?

My reasoning.
the Y on 4.16Y tells me it is a Y configuration, therefore between the common point of my three windings and the ground, i will put a resistor and a current of 200A going through it from the Y winding common point to the ground.

- Now the voltage in a Y configuration is as follow VLine = 1.73 Vphase. A this point I am interested in the Vph which is; Vphase= Vline/1.73 => Vphase = 4160 /1.73 = 2402v. This voltage is the one i will have from the uncommon leg of one winding to the ground. At this point have ohm law of one unknown resistor in series with one winding with a voltage of 2402v across them. Since, the winding infos are not given i will neglect that and just divide my phase voltage by the limiting current doing so, R=2402/200 =12.01 ohm as suggested by Testguy correct or no? thanks
I think you have an error when choosing the voltage you selected in your calculation. You stated the transf is a delta wye, 13.8kv to 480y/277. So seeing how there is not a neutral on the hv side of the transformer, I am supposing the resistor is supposed to get connected to the low voltage side. And seeing how the device is called a neutral to ground resistor I think you would need to use the hot to neutral voltage of 277 for your calculation. And this makes more sense by the fact that, with a NGR you are trying to limit your fault current to ground, and the only continuity from phase to ground is via the neutral.
I havent dealt performed a calculation to size a NGR before but I thought I might be right and wanted to help. Someone let me know if Im right!  Reply With Quote

7. Originally Posted by TestingProToBe I think you have an error when choosing the voltage you selected in your calculation. You stated the transf is a delta wye, 13.8kv to 480y/277. So seeing how there is not a neutral on the hv side of the transformer, I am supposing the resistor is supposed to get connected to the low voltage side. And seeing how the device is called a neutral to ground resistor I think you would need to use the hot to neutral voltage of 277 for your calculation. And this makes more sense by the fact that, with a NGR you are trying to limit your fault current to ground, and the only continuity from phase to ground is via the neutral.
I havent dealt performed a calculation to size a NGR before but I thought I might be right and wanted to help. Someone let me know if Im right!
He is answering a separate question listed in his post with his voltage to ground as 2.4kV, where the original post had a question that was 277V.  Reply With Quote

codes and standards, electrical calculations, grounding systems, low voltage, nec, neta exam questions, neta exam tips, transformers Related Content 