×

# What is the theoretical maximum symmetrical fault current?

###### Jump to latest post
1.  Junior Member
Join Date
May 2015
Posts
4
Reputation ## What is the theoretical maximum symmetrical fault current?

What is the theoretical maximum symmetrical fault current that would be available at the secondary terminals of a 3-phase 12,470-480Y/277V, 1000kva, 6.25% impedance transformer?  Reply With Quote

2. Fault Current = Full Load Amps (FLA) / % Impedance (Z)
FLA = VA / L-L Voltage x 1.732

Here is a thread that explains the equations step by step -> http://testguy.net/threads/1341-Easy...-fault-current  Reply With Quote

3.  Junior Member
Join Date
Jan 2015
Posts
24
Reputation   ## Short-circuit

Here the information:
12,470-480Y/277V
1000kVA, 6.25% impedance

another way:

For a impedance of 6.25%, your necessary voltage will be 6.25% of 480 Volts = 30 Volts
What that means:
With secondary shorted, if you apply 30 Volts, you will have full transformer current, which is: (remeber to multiply by 1000 (KVA to VA conversion)
I = 1202.85 A
from here you calculate your transformer Impedance
Z = V/I......Z = 30/1202.85.......Z = 0.025 Ohms.
I = V/Z.......I = 480/0.025 = 19200 A  Reply With Quote

4.  Junior Member
Join Date
May 2015
Posts
4
Reputation Thanks for the help.  Reply With Quote

5.  Junior Member
Join Date
Apr 2018
Posts
16
Reputation  Originally Posted by joaogemal Here the information:
12,470-480Y/277V
1000kVA, 6.25% impedance

another way:

For a impedance of 6.25%, your necessary voltage will be 6.25% of 480 Volts = 30 Volts
What that means:
With secondary shorted, if you apply 30 Volts, you will have full transformer current, which is: (remeber to multiply by 1000 (KVA to VA conversion)
I = 1202.85 A
from here you calculate your transformer Impedance
Z = V/I......Z = 30/1202.85.......Z = 0.025 Ohms.
I = V/Z.......I = 480/0.025 = 19200 A
The link that Second Gen posted doesn't state anything about the additional steps you took dealing with the impedance.

Can anyone confirm?  Reply With Quote

6.  Junior Member Pro Subscriber
Join Date
Oct 2015
Posts
1
Reputation ## Motor winding Results

Winding test results on a motor indicate possible degradation when the output waveforms show:
Winding waveform symmetry
Noticeable difference in winding waveforms
Chopped waveforms on grounded windings
Chopped waveforms on phase ungrounded windings

Having trouble getting an answer for this.  Reply With Quote

arc flash, electrical theory, fault current, neta exam questions, safety, transformers Related Content 